Seeing temperature alerts as soon as booting of the switch.
%C6KENV-4-MINORTEMPALARM: module 9 asic-10 temperature crossed threshold #1(=90C). It has exceeded normal operating temperature range.
We could see multiple asics on the line card having high temperature values and had a thorough check on environment sighting its not just limited to a particular asic and mostly likely not a hardware issue with card.
However there was nothing blocking the air-flow or there was nothing wrong with air conditioning of the data center. Also slot covers were installed on all empty-slots.
The issue was resolved after removing blank slot cover and installing filler plates (WS-X6K-SLOT-CVR-E which simlar to a dummy line card) in empty adjacent slot as recommended per hardware installation guide.
Chassis Slot Filler Restrictions for WS-X68xx and WS-X69xx Modules
If you are installing one or more of the WS-X68xx or WS-X69xx modules in your chassis, the slots directly adjacent to these modules (above and below or to the left and to the right) must contain either another module or switching-module filler plates (Cisco part numbers WS-X6K-SLOT-CVR-E or SLOTBLANK-09). If either adjacent slot is unused and currently has a blank slot cover (Cisco part number WS-X6K-SLOT-CVR) installed, you must remove the blank slot cover and replace it with a switching-module filler plate for NEBS compliance.
Hope this helps if you ever encounter similar issue.
“Use Serviceability Features to Troubleshoot your Cat9K as a Cisco TAC Engineer”
This special event is open only to Cisco Customers and Partners.
Many pages in the Cisco Community are accessible only to Cisco customers, partners, or logged in ...
i am new to this and learning by doing on the waywhat i try to achieve in the moment is to reroute the port 80 on pc 0to 100 on pc 0 this is how i forward external internet trafic to itip nat inside source static tcp 10.1.1.1 100 interface Cellular0/...
hi everyone this topic is been posted few time and there were some solutions but its not working. Below are the logs from a access layer switch(c3650) which blocks the trunk port. this switch is connected to a layer 3 switch(c3850) in that switch its...