Recently purchased 2 Nexus 7009 Chassis for our datacenter. We are wanting to mount side by side in two post racks. Is this a supported mounting config since the 7009 uses side to side airflow. The clearance between the chassis is approximately 7 inches.
Required clearances between the Cisco Nexus 7009 chassis and the edge of its rack or interior of its cabinet are as follows:
11 inches (27.9 cm) between the side of the chassis and the interior of the cabinet or the clearance area for the next rack or cabinet (required for side-to-side airflow with all types of racks or cabinets).
We delivered a partner enablement training session in September 2021 to share the ACI upgrade Best Practices.
The slide deck is enclosed here for wider audience in the community, it provides more details in terms of the best practices, tools and co...
What is Cisco ACI Anywhere?What are ACI connectivity options for managing Primary On-Prem DCs?What are ACI options for extending your Data center to secondary remote locations (Physical)?How ACI provides centralized network policy framework for workloads ...
Cloud Networking Community on Cisco Customer Connection
Join our community!!
As a valued Cisco Cloud Networking (former DCN) customer, you can be part of Cisco Customer Connection Program (CCP), Cisco’s global online community program. Connect ...
Join us for a live demo of Cisco Intersight Cloud Orchestrator to learn how you can simplify the orchestration and automation of your infrastructure and workloads across your hybrid cloud environment. We will take a closer look at Cisco Intersight Cloud O...
Hybrid Cloud Demo Series: Simplify Orchestration of Your Infrastructure and Workloads
Tuesday, September 7, 202110:00 am Pacific Time(San Francisco, GMT-08:00)Join us for a live demo of Cisco Intersight Cloud Orchestrator to learn how you can simpli...